|Home | Articles | Forum | Glossary | Books|
Forum (Message Board)
Observe the requirement outlined above for disconnecting means, controller, and overload units. Use wire with an ampacity of at least 125 percent of the full-load current of the motor. For long circuits use wire larger than required by NEC in order to avoid excessive voltage drop. If the circuit to the motor is long, and you use wire that's too small, you may have only 100 volts at the motor during the starting period instead of nearly 120 volts. The motor may not start, or if it does it will deliver significantly less than its rated horsepower. The Table below shows the wire size to use at various distances from service equipment to motor, assuming the wire has an ampacity of at least 125 percent of the full-load current shown on the nameplate of the motor. All distances are one-way. The table is for single-phase motors only.
|PREV:||Motor Circuit Requirements||NEXT:||HOME|